Each closed-head sprinkler is held closed by either a heat-sensitive glass bulb (see below) or a two-part metal link held together with fusible alloy such as Wood’s metal and other alloys with similar compositions. The glass bulb or link applies pressure to a pipe cap which acts as a plug which prevents water from flowing until the ambient temperature around the sprinkler reaches the design activation temperature of the individual sprinkler. Because each sprinkler activates independently when the predetermined heat level is reached, the number of sprinklers that operate is limited to only those near the fire, thereby maximizing the available water pressure over the point of fire origin.
The bulb breaks as a result of the thermal expansion of the liquid inside the bulb. The time it takes before a bulb breaks is dependent on the temperature. Below the design temperature, it does not break, and above the design temperature it breaks, taking less time to break as temperature increases above the design threshold.
|Maximum Ceiling Temperature||Temperature Rating||Temperature Classification||Color Code
(with Fusible Link)
|Liquid Alcohol in Glass Bulb Color|
|38 °C||57-77 °C||Ordinary||Uncolored or Black||Orange (57 °C) or
Red (68 °C)
|66 °C||79-107 °C||Intermediate||White||Yellow (79 °C) or
Green (93 °C)
|107 °C||121-149 °C||High||Blue||Blue|
|149 °C||163-191 °C||Extra High||Red||Purple|
|191 °C||4204-246 °C||Very Extra High||Green||Black|
|246 °C||260-302 °C||Ultra High||Orange||Black|
|329 °C||343 °C||Ultra High||Orange||Black|